Question about Honeywell Programmable Thermostat Heater
The unit is in the basement is humming. We did shut the unit off and turned it back on the humming and flame reaapearred in 15 minutes or so. There is also a smell coming from the vents.
Sounds like the circulating fan on your furnace is not running. This will cause the furnace to shut down due to overheating, and you can smell the overheating as well. You will probably have to press a reset button on the burner to clear the overheat shutdown. Check the fan belt if there is one. If no belt you have an integral motor. Remove all power from the system and make sure the fan spins freely. If it doesn't, try to work some oil into the bearings. These things always fail on a holiday, but if you can't get the fan spinning you're going to have to call in a HVAC specialist.
Posted on Jan 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 10, 2015 | Honeywell Programmable Thermostat Heater
Jul 30, 2014 | Dometic 3109228.001 Duo Therm Comfort...
Sep 23, 2011 | Heating & Cooling
Jan 21, 2011 | Pitco Frialator SG18S Deep Fryer
Jan 07, 2011 | Goodman GMS90703BXA Heater
Nov 28, 2010 | Goodman CLQ36AR49 Air Conditioner
May 07, 2010 | Heating & Cooling
Sep 01, 2009 | Heating & Cooling
Sep 19, 2008 | Bosch 1600H-LP Liquid Propane AquaStar...
Aug 17, 2008 | Amana Heating & Cooling
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
234 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: