Question about LG LSC121PMA Split System Air Conditioner
My airconditioner internal fan on my split system stopped working in the middle of the night and i have reset the power and checked the gas pressure and it is sitting at 0 degress celcius the evaporator is getting cold and the compressor and condensor fan are both running but for some reason the internal fan will not go anyone have any ideas
Check that the fanmotor can spin freely. If not, can be caused by seized bearing on left side of fanblade, or foreign object, insect nest stuck in fanblade. If however it spins freely, check that fanmotor is being supplied with voltage (you sound technically capable of operating a volt meter). If power is supplied, fanmotor is faulty and needs replacing. If no voltage, problem lies with the pc board. If you know someone who is capable let them check the relays on the board. Also you can check that all plug on connectors are making good connection.
Posted on Mar 05, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 25, 2013 | Panasonic Heating & Cooling
Oct 25, 2011 | LG LA185HV Split System Air Conditioner
Nov 13, 2010 | LG LA141CE Split System Air Conditioner
Oct 04, 2010 | LG LSC121PMA Split System Air Conditioner
May 18, 2010 | LG Art Cool LA181CNW Split System Air...
Nov 16, 2009 | GE Zoneline AZ38H12DAD Split System Air...
May 28, 2009 | Heating & Cooling
May 19, 2009 | LG LSC121PMA Split System Air Conditioner
Jan 05, 2009 | LG LS-L1210CL Mini Split Air Conditioner
423 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: