Question about Siemens /ITE 100Amp 3-pole molded circuit breaker
Half the breakers in my Siemans 100A 24 circuit box show zero voltage - no main entrance breaker pop off. Reset main and all work for a while. I replaced the main and everything worked for several months - now old problem is back. I purchased the panel and main breaker from Home Depot for under 60 bucks. The main breaker part number replacement from Siemans is over 170 bucks - something isn't right here. Are we looking at QC rejects or cheap look alikes? Any thoughts about what is wrong?
Sounds to me as if you are losing one side of the line inside the meter enclosure , possibly due to lose connection or corrosion on terminals in base i think i would remove meter and have a look see if you are not comfortable to do this have an electrician to do ck
Posted on Jan 01, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 19, 2017 | GE Electrical Supplies
Nov 21, 2015 | Cars & Trucks
Apr 06, 2015 | Dryers
Jan 01, 2012 | Dryers
Jan 21, 2011 | Cutler Hammer 200 Amp Circuit Breaker...
Dec 05, 2010 | Siemens 100 Amp Main Breaker Renovation...
Nov 28, 2010 | Heating & Cooling
Sep 21, 2009 | Siemens #MP120GF 20A SP GFI Breaker
Jul 14, 2009 | NRS Siemens Fxd63s250a Circuit Breaker...
Jan 30, 2009 | Stiebel Eltron TEMPRA 12 Tankless Water...
341 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: