I have a Leviton 5634 two rocker switch that I'm using to replace an old double switch that controls two lights. There are 1 black, 1 red, and 1 white wire in the light switch box. The white wire is...
Review old switches:
Two old switches > each has 2 wires
Old switch 1 > Red and White
Old switch 2 > Black and White
The same white wire connects to both switches, so effectively they count as 1 wire
This means you have 3 wires ... 1 White, 1 Red, 1 Black
Each switch controls a separate load (light, fan, motor)
New Leviton double-rocker switch:
-Leviton has 2 Brass-colored screws on one side, and these screws are connected together by a brass plate >> your Hot wire will connect to brass screw
-Leviton has 2 Silver-colored screws on other side, and neither of these screws are connected in any way >> the wires going to each load will connect on a different screw on this side of switch.
Hot wire: Each box in your house has exactly 1 hot wire that is connected back to breaker box. This is true for all boxes (excluding boxes that have a 3-way & 4-way switches).
We need to identify Hot wire.
-By code the Hot wire is black for identification purposes ... but your box sounds like maybe the Hot wire is White.
-If your Hot wire is white, that is NOT an immediate safety issue ... it will not cause a fire or malfunction ... it is a code violation ... because code requires things be uniform so next electrician knows what previous guy did. So some day, electrician working outside grabs wrong color wire, and wow. I say this so you know.
Identify Hot wire:
-Pull 3 wires up so they can be tested
-Turn on power
-Use ordinary tester, or old lamp with plug cut off and wires stripped back
-Tape tester lead to sticks so hands are away from voltage
-Power is on. Don't stand in water or touch metal pipes, and you're fine.
-You have 3 wires in box + ground wire
-Test all 3 wires to bare ground wire >> when tester lights up, that is Hot wire ... testing is complete
Connect wires to Leviton double-rocker:
-Power is OFF.
-You have 3 wires - 1 White, 1 Black, 1 Red >> one is Hot wire, the other two wires go to load
-Hot wire connects to Brass-colored screws on new Leviton.
-Brass colored screws are connected together by a brass plate so the Hot does not need to connect to both brass screws.
-The other two wires connect to Silver screws on other side of new Leviton switch
-One wire goes to each silver screw
-Connect bare ground wire to green screw.
-Push wires back into box. Use eraser end of pencil if needed.
-Make sure ground wire is back and away from screws on switch
Sep 30, 2010 |
Leviton Light Switches & Dimmers