Question about Carrier 38CKC042 Air Conditioner
My furnace stopped working and after 2 days workt for a while and is not working again. i see green light on and hear sound but is not blowing air. it is keeprite brand and model n9mp1o5ob12a2. what can i do ?
This may sound not useful but the first thing to try is turn off the breaker or fuse to the feed for the furnace for 1 minute and turn back on and listen and note exactly what it does from there and will have better idea how to help and this might fix the problem try and let me know th results
Posted on Jan 01, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 29, 2015 | Heating & Cooling
Mar 04, 2011 | Goodman GMS90703BXA Heater
Feb 19, 2011 | Heating & Cooling
Jan 07, 2011 | Coleman Propane Forced Air Heater...
Dec 06, 2010 | 2007 Chevrolet Tahoe
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Nov 30, 2010 | Goodman GMS80903BNA Heater
Jun 01, 2009 | Weather King 10AJA2501AH Air Conditioner
Apr 13, 2009 | Heating & Cooling
545 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: