Question about Intertherm P3RA-048K Air Conditioner
Furnace that won't kick out of cycle just keeps running
Hello , I think I can help , with the power off to the unit disconnect the wiring on the thermostat and remove it make sure the wires are not touching, turn power back on and see if the unit still runs , if not thats the problem pickup a new tstat , if it still runs then you have a sticking contactor in the control panel of the unit , all of the componets in the unit feed off the contactor and its easy to find its about two inches by 3 inches. There are a set of contacts in it that will be blackend or burnt , remove, label all wires where they were going and pickup a new one at any Hvac, A/C warehouse.
Hope that helps , let me know how it turned out.
Posted on Dec 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 20, 2014 | Intertherm Heating & Cooling
Oct 24, 2013 | Coleman Intertherm Nordyne Miller Furnace...
Dec 21, 2012 | Heating & Cooling
Aug 15, 2012 | Intertherm Heating & Cooling
Jul 25, 2010 | Intertherm Heating & Cooling
Dec 24, 2009 | Intertherm P3RA-048K Air Conditioner
Apr 23, 2009 | Intertherm P3RA-048K Air Conditioner
Dec 06, 2008 | Intertherm Heating & Cooling
Nov 15, 2008 | Intertherm Heating & Cooling
94 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: