Question about M20 X-Treme Radar Detector
My baxi solo 3 50pf boiler is giving me grief! everything seems to work ok ie pump, 3 port valve etc, however, the boiler starts when request ( via timer) the burner ignites and runs for about 1 min. then shuts off, fan still runs, then burner will cut in again for about 1 min and so on. Rads are warm but never get hot, water gets luke warm. I have also noticed pump runs continuously 24/7?!? Any ideas?
SOURCE: Baxi solo 3 70pf boiler problem
This happened to me and it was a rubber pipe inside had perished so it was detecting a loss of pressure. You can see it if you take the main cover off and also the front clipped on cover. Its at the top on the right. You need to replace it with heatproof pipe. Good luck!
Posted on Jan 05, 2010
Tips for a great answer:
Jan 23, 2014 | Honeywell Programmable Thermostat Heater
Feb 09, 2011 | Heating & Cooling
Nov 26, 2010 | Heating & Cooling
Oct 27, 2010 | Kitchen Ranges
Dec 31, 2009 | M20 X-Treme Radar Detector
May 15, 2009 | Water Heaters
Mar 01, 2009 | Water Heaters
Oct 29, 2008 | Heating & Cooling
1,186 people viewed this question
Usually answered in minutes!