Question about SySTOR Systems (400S52) Burner
I have had one solonoid coil that became weak and would not hold the valve open, most likely cause is the relay in the controller has oxidised or pitted contacts giving momentary flame often confused for failing photo cell, monitor voltage on coil, probably need new controller about $300 NZ
Posted on Apr 21, 2009
a 6ya Technician can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Technician (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 16, 2013 | Briggs & Stratton Pressure Washer...
Mar 02, 2013 | Heating & Cooling
Dec 29, 2010 | All-Pro Kerosene Garage Shop Heaters - All...
Sep 25, 2010 | Heating & Cooling
May 25, 2010 | Garden
Jan 27, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Dec 15, 2008 | Heating & Cooling
Nov 15, 2008 | SySTOR Systems (400S52) Burner
201 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: