Question about Electrical Supplies
I have installed a 3 gang grid dimmer, with 12 spots on one switch (grid 750w), 6 on another (500w) and 9 on another (500w). The dimmer with the 9 spots has blown twice. once without warning and then a light bulb exploded and the switch wont work anymore. Any ideas on how to fix without replacing the dimmer for the second time in 3 weeks?
In addition to an individual rating per dimmer, these dimmers have a total recommended rating based on the size of grid used. Assuming you've got three in a double box - the total combined load is 1000W of tungsten or 700W of LV fittings. It looks to me like your trying to dim too much in a limited space and generating too much heat.
Posted on May 28, 2009
Also look at what your dimming, if it's gu10 lamps these can downrate your dimmer by as much as 50% in some cases. Check with the manufacturer to be sure.
And the above post is right, you'r way overheating the dimmers.
Look intogetting a remote pack, or for a cheaper option replace lamps with a lower wattage e.g 35w.
Posted on Feb 26, 2010
Too much load? Disconnect some spots and see what happens.
Posted on Feb 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 22, 2015 | Electrical Supplies
Sep 16, 2014 | Electrical Supplies
Sep 05, 2013 | Cooper Industries Cooper Wiring 2158V 3...
Jan 08, 2013 | Lutron Electrical Supplies
May 28, 2011 | Cooper Industries Cooper Wiring 2158V 3...
Dec 22, 2010 | Solar Carlon Thyrocon Dimmer Controls...
Feb 14, 2010 | Cooper Industries Cooper Wiring 2158V 3...
Jan 09, 2010 | Lutron Claro Screwless 2 Gang Wall Plate...
525 people viewed this question
Usually answered in minutes!