Question about Heating & Cooling
SOURCE: I want to adjust the
To enter the adjustment mode, press the UP, DOWN, and I buttons simultaneously for three seconds. Press the I button until the feature requiring adjustment is displayed:
HL High Limit.
LL Low Limit.
Ldf Low Limit differential.
Then press the UP and/or DOWN buttons to move the set point to
the desired value. After 60 seconds without any button inputs, the
control will automatically return to the READ mode.
(copied from honeywell's instructions)
to clarify the differential is cut in minus the cut out.
Hope i can be some help to you.
Posted on Apr 21, 2008
Tips for a great answer:
Nov 12, 2014 | Water Heaters
on Dec 08, 2009 | Heating & Cooling
Oct 11, 2014 | Water Heaters
Feb 02, 2013 | Water Heaters
Nov 22, 2012 | General Electric GE SmartWater Household...
Feb 19, 2011 | Heating & Cooling
Jan 29, 2010 | Honeywell L4103A1019 combination aquastat....
Oct 08, 2008 | Water Heaters
Apr 21, 2008 | Heating & Cooling
Apr 30, 2017 | Heating & Cooling
202 people viewed this question
Usually answered in minutes!