Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: I want to adjust the
To enter the adjustment mode, press the UP, DOWN, and I buttons simultaneously for three seconds. Press the I button until the feature requiring adjustment is displayed:
HL High Limit.
LL Low Limit.
Ldf Low Limit differential.
Then press the UP and/or DOWN buttons to move the set point to
the desired value. After 60 seconds without any button inputs, the
control will automatically return to the READ mode.
(copied from honeywell's instructions)
to clarify the differential is cut in minus the cut out.
Hope i can be some help to you.
Posted on Apr 21, 2008
Tips for a great answer:
Nov 12, 2014 | Water Heaters
on Dec 08, 2009 | Heating & Cooling
Oct 11, 2014 | Water Heaters
Oct 05, 2017 | Honeywell L8124G1020 Triple Aquastat Relay...
Nov 22, 2012 | General Electric GE SmartWater Household...
Feb 19, 2011 | Heating & Cooling
Jan 29, 2010 | Honeywell L4103A1019 combination aquastat....
Oct 08, 2008 | Water Heaters
Apr 21, 2008 | Heating & Cooling
211 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: