Question about Heating & Cooling
Sounds like your t-stat is failing you. Here is a test you can do. Take the front cover off. Locate the R terminal and the W terminal. Get your self a short piece of wire small diameter say 18 gauge. Now take your wire and jump across the two terminals hold them there and if you hear your furnace kick on then the t-stat is bad. let me know what you find out. ken
Posted on Dec 28, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2017 | Heating & Cooling
Feb 09, 2014 | Heating & Cooling
Aug 23, 2017 | Heating & Cooling
Jun 18, 2017 | Heating & Cooling
Mar 20, 2010 | Heating & Cooling
Jan 31, 2010 | Dayton Gas Furnace Heater
Jan 06, 2010 | Honeywell Programmable Thermostat Heater
Dec 05, 2009 | Dayton (3E407) Heater
Nov 22, 2008 | Jandy Aqualink - Rs24 One Touch Pool / Spa...
Oct 17, 2018 | Heating & Cooling
290 people viewed this question
Usually answered in minutes!