Question about Heating & Cooling
Sounds like your t-stat is failing you. Here is a test you can do. Take the front cover off. Locate the R terminal and the W terminal. Get your self a short piece of wire small diameter say 18 gauge. Now take your wire and jump across the two terminals hold them there and if you hear your furnace kick on then the t-stat is bad. let me know what you find out. ken
Posted on Dec 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 09, 2014 | Heating & Cooling
Aug 23, 2017 | Heating & Cooling
Jun 18, 2017 | Heating & Cooling
Mar 20, 2010 | Heating & Cooling
Jan 31, 2010 | Dayton Gas Furnace Heater
Jan 06, 2010 | Honeywell Programmable Thermostat Heater
Dec 15, 2009 | Honeywell Programmable Thermostat Heater
Dec 05, 2009 | Dayton (3E407) Heater
Nov 22, 2008 | Jandy Aqualink - Rs24 One Touch Pool / Spa...
289 people viewed this question
Usually answered in minutes!