Question about Empire GWT-25 Wall Mounted Panel Heater
We just installed an Empire gas wall heater. The pilot lights, but the main burners and fan will only run for about 1 minute and then they shut off. They do not start back up even when we skip the thermostat and make direct contact with the units wires. We vented the unit out the side of the house, with about 1 foot of venting going up the top before the 90* turn. Is this distance inadequate and causing the emergency shut off to trip? If so, how much venting is needed before turning out the side wall? Or must it vent directly up through the roof? Any other things that may be causing this to occur.
It sounds like the gas valve is dropping out. Make sure the system is venting the exhaust(no restrictions). Then make sure all your wiring connections in the unit are tight. In a millivolt system if all wiring connections aren't tight and clean your circuit will drop in millivolts and the gas valve will drop out. The gas valve requires a certain millivolt to stay open. I hope I was of some assistance!! Good luck!!
Posted on Nov 29, 2009
Tips for a great answer:
Mar 02, 2012 | Empire ECS HearthRite HR18MN Heater
Dec 02, 2011 | Empire Heating & Cooling
Oct 30, 2011 | Empire DV-35 Heater
Apr 11, 2011 | Empire Direct Vent Wall Furnace;...
Feb 04, 2011 | Empire GWT-50 Wall Mounted Panel Heater
Feb 02, 2011 | Empire Heating & Cooling
Nov 29, 2009 | Empire Direct Vent Wall Furnace Millivolt...
Oct 07, 2009 | Reddy Heater-10-12-15,000 Btu L.P.
194 people viewed this question
Usually answered in minutes!