Question about York Yankees Bedding MLB Comforter
I have a York high efficiency furnace that is not firing all the the time. The unit is about 4 to 5 years old & has been doing this for a few months now and getting progressively worse. (model # GM9S08B12DH11G) The trouble code light inside is blinking a rapid red, indicating a Twinning Error, Incorrect 24V Phasing.
Has anyone worked on this furnace because the error would indicate that the positive 120 volt and the neg 120 volt is swapped , these units will also do this when the ground wire to the furnace or gas valve or furnace or @ the panel is lose , corroded , or missing , the gnd must be present to open valve , I am aware that ac is is not usually polarity sensitive but in this case it most certainly is ...have seen many time and know it to be true
Posted on Jan 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 26, 2009 | York Yankees Bedding MLB Comforter
Nov 18, 2009 | York Yankees Bedding MLB Comforter
Feb 01, 2009 | York Yankees Bedding MLB Comforter
Jan 16, 2009 | York Yankees Bedding MLB Comforter
Jan 10, 2009 | York Yankees Bedding MLB Comforter
Dec 27, 2008 | York Yankees Bedding MLB Comforter
Dec 03, 2008 | York Yankees Bedding MLB Comforter
833 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: