Question about Heating & Cooling
How do you take the cover off to get to the thermal coupling nut on top? I can't seem to get it out to replace.
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Its in the bottom of the heater behind the vent cover . I don't know where you are but your local gas utility will come out and lite this for free.
Posted on Dec 23, 2007
First make sure this is a heater set up for a remote mounted thermostat. If so, the gas valve has 3 screws labeled TH (thermostat) and TP (thermopile) that's the flame sensor with 2 wires coming off it, I don't know where the goofy name comes from. there will be one screw that has both, usually the top one. Wire accordingly. The new valves have a solenoid on the bottom. this connects to the high temp. sensor up top. It has 2 wires on it, one connects to the thermostat wire, the other goes to the screw with TH and TP. Or you can skip it and connect the wire from the back of the valve to the Th and TP screw. Make sure the thermostat wires aren't pinched somewhere, thus eliminating the thermostats control.
Posted on Mar 02, 2008
if the pilot light stays lit, but the burners don't kick on, it's a problem with the thermostat or thermostat wiring, or a problem with the valve inside the gas actuator
Posted on Oct 25, 2008
SOURCE: How to reset vent safety switch
the reset is at the top left side of the furnace. take the cover off n press the red button. the switch could be failing but CHECK drafting through the furnace. hold a flame at the top of the furnace n make sure its pulling inward. u could have a blocked vent pipe or vent cap which will cause excessive heat n tip the safety switch. good luck!
Posted on Nov 24, 2009
Tips for a great answer:
Oct 30, 2017 | Williams Heating & Cooling
Dec 01, 2016 | Williams Heating & Cooling
Dec 08, 2015 | Williams Heating & Cooling
Feb 16, 2015 | Williams Wall Heaters: 50,000 BTU/Hr...
Mar 04, 2013 | Williams Furnace. 35,000 Btu/hr Monterey...
Feb 19, 2013 | Williams 14,000 Btu/hr Direct-Vent Furnace...
Apr 03, 2010 | Williams 1403622 Gas Compact Heater
Jan 11, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Oct 09, 2009 | Williams 1403622 Gas Compact Heater
Aug 31, 2017 | Heating & Cooling
Sep 20, 2018 | Heating & Cooling
514 people viewed this question
Usually answered in minutes!