Question about Panasonic WhisperWarm FV-11VHL1 Compact Heater
Our Panasonic Vent/Heater/Room Light/ Nitelight was professionally installed about a year ago. It has functioned flawlessly...until now. The heater was left on for apparently too long, and the thermal cutoff switch has stopped the heater from turning back on. The owner's manual is no help--it just has info on the proper installation. Is there a way to "reactivate" the switch? I see no switch inside the unit when I removed the cover, so I don't know whether the swich is designed to be replaced, like a one-time fuse.
Looking forward to an answer--the bathroom is getting COLD in the morning!
I had the same problem and mine was cause by a blown fuse. It's not too hard to fix. Remove the cover by pulling down and squeezing the wire arms on each side. You need a VERY long screwdriver to remove the entire motor/fan/light assembly from the housing (8 screws total). Place the assembly on the floor and look for the fuse on top. The fuse is on the motor, not near the heater portion. It is a ceramic, not glass, cylindrical fuse, 20 amps, 125 volts. This fuse is sold as a microwave oven fuse & costs about 2 bucks at a hardware store. Replace, reinstall, and you're done.
Posted on May 21, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2017 | Williams Heating & Cooling
Jan 05, 2017 | Reddy Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Jan 04, 2017 | All-Pro Heating & Cooling
Jan 03, 2017 | Heating & Cooling
Jan 01, 2017 | Heating & Cooling
Dec 28, 2016 | Heating & Cooling
Jan 11, 2015 | Heating & Cooling
Nov 03, 2014 | Heating & Cooling
Jun 23, 2014 | Heating & Cooling
1,445 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: