Question about Rinnai Toyostove Direct Vent Heater: Laser 30 Toyostove Direct Vent Heater Shipping
The technical data I have on the Monitor 2200 lists the following for an error code 13:
Failure of ignitor, solenoid pump or circuit board.
Incorrect wiring or flame rod touches to burner parts.
Air pressure switch or overheat open.
I would test the ignitor first, as that's likely the easiest, cheapest thing.
Then work to the pump, flame rod etc.
If you're not familar with the insides of one of these units, i'd recomend having the unit serviced by a qualified technician.
Helping Hands Services
Posted on Oct 27, 2009
EE13 on a Monitor is one thing. The same code on a Toyostove is completely different. A Monitor EE13 means there was no flame at ignition. On a toyostove EE13 is the burner thermistor.
On the Monitor I would check my fuel tank. On the Toyo you may have to have the dealer help you, as it could be something easy like a very cold day or more complicated as a main circuit board.
Posted on Jan 06, 2009
EE13 on a monitor heater means the flame rod couldn't detect fire during it's 300 second cycle. I'd start by cleaning the flame rod and making sure there are no obstructions in the exhaust flue. Also, the 2200 is known for clogging the 1/2 mm oil line that runs between the oil pump and the burner pot.
Posted on Dec 30, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 20, 2014 | Health & Beauty
Nov 06, 2017 | Walgreens Blood Pressure And Pulse Monitor
Jan 25, 2011 | Walgreens By HoMedics Automatic Wrist...
Sep 09, 2010 | Omron Model HEM 432C Manual Inflation...
Aug 19, 2010 | Omron Model HEM 432C Manual Inflation...
Dec 15, 2009 | Omron Hem 712CLCN2 Cuff Blood Pressure...
Feb 21, 2009 | Omron Automatic Blood Pressure Monitor...
Jan 18, 2009 | Health & Beauty
671 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: