Question about Goodman CKL36AR36 Air Conditioner
When the set temperature is reached the outside condenser shuts off but the air handler keeps running (for hours). The only way I can turn it off is by throwing the circuit breaker. The problem started a few weeks ago. I replaced the batteries in the thermostat and everything was working fine. Now the problem is reoccurring.
As long as the t-stat fan switch is in the auto position the problem sounds like fan relay is stuck. It looks like a little black box about 2 inches square. Has 5 positions on it two of them are for 24 volts.
Be sure you turn off power before pulling it out. Make note of the arrangement of the wires maybe label as you remove them. ken
Posted on Dec 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 28, 2015 | Heating & Cooling
Jan 17, 2013 | Gibson Heating & Cooling
Nov 15, 2012 | Goodman Manufacturing Goodman ARUF303016...
Sep 07, 2011 | Heating & Cooling
Jul 13, 2011 | Heating & Cooling
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Dec 08, 2010 | Honeywell Programmable Thermostat Heater
Sep 02, 2009 | Heating & Cooling
May 19, 2009 | LG Heating & Cooling
Aug 14, 2008 | Heating & Cooling
2,232 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: