Question about Siemens 2 single pole 15 amp breaker
Two 15 Amp circuit breakers won't reset after they were overloaded. How can I reset those?
Unplug the appliance that is overloading the breaker.
reset the breaker, plug in the appliance. if the breakers pops, then the appliance is the problem.
you may want to check the appliace manual and make sure the breaker is rated for the appliance you are using.
Posted on Dec 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 04, 2014 | Siemens Electrical Supplies
Aug 30, 2014 | Siemens Ite Twin Q1515 Circuit Breaker...
Jun 09, 2013 | Electrical Supplies
Sep 18, 2011 | Siemens Ite Twin Q1515 Circuit Breaker...
Dec 20, 2010 | Siemens 200 Amp Main Breaker 30 Spaces 40...
Nov 20, 2010 | Sea and Sea Blue Sea 7327 Circuit Breaker...
Sep 18, 2010 | Siemens 2 single pole 15 amp breaker
Jan 25, 2010 | Bulldog Pushmatic 31115 P115 15 Amp...
Jan 07, 2010 | Siemens /ITE 100Amp 3-pole molded circuit...
Dec 01, 2008 | Siemens 2 single pole 15 amp breaker
703 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: