Question about Jenn-Air JED8430 Electric Cooktop
This answer does not solve the question regarding what to do with the red wire??
Posted on Jun 18, 2008
You do need a 208/240 volt supply from your service panel. The green is ground, white is nuetral, and the red and black should measure 120 volts each to ground or 240/208 between each other. It is normal for most breaker panels to supply 208/240 between adjacent insulators. If you are only getting 1/2 of that then the circuit breaker may not be straddling the insulator bar but be 1/2 notch out and both breaker pins contacting the same 110 supply.
Posted on Apr 16, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 07, 2011 | Whirlpool GJC3034 Electric Cooktop
Mar 20, 2011 | Jenn-Air JED8230 Electric Cooktop
Nov 08, 2009 | Jenn-Air JED8430 Electric Cooktop
Jan 28, 2009 | Jenn-Air JED8430 Electric Cooktop
Nov 07, 2008 | Cooktops
Sep 06, 2008 | Jenn-Air JED8430 Electric Cooktop
Nov 16, 2007 | Jenn-Air JED8430 Electric Cooktop
944 people viewed this question
Usually answered in minutes!