Question about Heating & Cooling
Hello - my Rheem Criterion II (old model) would not ignite the flame.It worked until a couple of days ago. When I open the cover and startthe furnace, the green LED is blinking twice then pause. According tolabel, the pressure switch is open. How can I fix this? Do I need toinstall a new pressure switch? Please advise.
What you need to do is take and inspect the hose that goes to the pressure switch and make sure that it is not dry rotted. if it is and the combustion blower is running then firsat try to cut the hose down and slip on a better piece of rubber. If not then replace the hose,
Posted on Dec 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2015 | Heating & Cooling
Jan 08, 2013 | Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 11, 2011 | Heating & Cooling
Apr 04, 2010 | Heating & Cooling
Jan 05, 2010 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Oct 29, 2009 | Rheem Paloma PH-20R IFSN / RTG-53PVN...
Mar 10, 2009 | Goodman GMS90703BXA Heater
524 people viewed this question
Usually answered in minutes!