Question about Heating & Cooling
What it sound like is that your sons room is the closest room to the boiler and is getting too much of the heates water. your room is probebly the room in the middle and your daughters is the last one. Lets start bye taking and shutting down the valves in youe sons room and or adjusting the circuit setters which is what you probebly have . THey should by on the return line and you can adjust them by just closing them down a little bit at a time or if you have a way to take the temperature of the return and the supply lines then you would try to shoot for around 10 delta t. look at the baseboard heaters where the water come in and that should be where you will find the circuit setters. Good Luck and have a Merrry Christmas
Posted on Dec 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 11, 2010 | Heating & Cooling
Aug 03, 2010 | Ruud Central System Air Conditioner
Jul 22, 2009 | Ruud UAKA042 Air Conditioner
May 26, 2009 | Heating & Cooling
Apr 02, 2009 | DeLonghi Pinguino PACL90 Portable Air...
Feb 23, 2009 | Ruud Central System Air Conditioner
Jan 25, 2009 | Heating & Cooling
Nov 16, 2008 | Intertherm Heating & Cooling
Aug 06, 2008 | Heating & Cooling
Aug 01, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
75 people viewed this question
Usually answered in minutes!