Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
Make sure G from indoor unit goes to G on thermostat for fan continous fan, if that doesn't work and you have 24 volts to R and C then the t'stat is bad.
For 2nd stage heat or aux.heat, on the indoor unit you need to make sure the wire W2 from the indoor unit goes to W2 on t'stat.
You don't need any wires from W1on the indoor unit to W1 at the t'stat because with a York heat pump Y1 is the contactor which turns the compressor on and you will get 1st stage heat, and for cooling the t'stat will also bring on O which is the (reversing valve) or cooling changeover relay for the cooling mode.
C = common usually black wire
R = hot usually red wire
Y or Y1 = contactor
W1 = 1st stage heat not needed for heat pump
W2 = Aux. heat indoor heat
G = fan
O = Cooling changeover relay
B = Heating changeover relay
L = System monitor
E = Emergency heat relay
Posted on Sep 17, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2013 | Honeywell Programmable Thermostat Heater
Jan 10, 2011 | Honeywell Programmable Thermostat Heater
Dec 15, 2009 | Honeywell Programmable Thermostat Heater
Jun 18, 2009 | Honeywell Electronic Programmable...
Mar 22, 2009 | Honeywell Programmable Thermostat Heater
Nov 24, 2008 | Honeywell Electronic Programmable...
Oct 24, 2008 | Honeywell Programmable Thermostat Heater
Oct 20, 2008 | Hunter Fan Company 5/1/1 Programmable...
Apr 28, 2007 | Honeywell Programmable Heat Pump...
791 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: