Question about Heating & Cooling
I have a Intertherm forced air gas furnace model#MGHA075ABFC-01 in my mobile home and recently after the burner fires up the blower comes on for a few seconds and shuts down and continues cycling as long as it keeps calling for heat. I understand that this is normal for the blower to shut down until the temperature is high enough in the heat exchanger but this cycling goes on for hours. The heat ducks get so hot, you can't touch them. Is there some sort of sensor or swith that might be malfunctioning and how can I test it? I have some electrical testing equipment. Thanks.......Guy
Check out the fan switch on the unit and make sure that its the correct one. it should cycloe on @ 120 degrees and cycle off around 100 degrees. Someone may have put in a different one and that is not the approve one.
Posted on Dec 23, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 16, 2015 | Heating & Cooling
Jun 25, 2015 | Intertherm Heating & Cooling
Feb 03, 2015 | Heating & Cooling
Feb 15, 2014 | Intertherm P3RA-048K Air Conditioner
Aug 08, 2017 | Intertherm E3EB010H Electric Furnac
Nov 08, 2011 | Intertherm P3RA-048K Air Conditioner
Nov 12, 2010 | Intertherm Heating & Cooling
Oct 20, 2009 | Intertherm P3RA-048K Air Conditioner
Jan 17, 2009 | Coleman Propane Forced Air Heater...
Apr 24, 2018 | Heating & Cooling
324 people viewed this question
Usually answered in minutes!