Question about Air Conditioners
I have a Intertherm forced air gas furnace model#MGHA075ABFC-01 in my mobile home and recently after the burner fires up the blower comes on for a few seconds and shuts down and continues cycling as long as it keeps calling for heat. I understand that this is normal for the blower to shut down until the temperature is high enough in the heat exchanger but this cycling goes on for hours. The heat ducks get so hot, you can't touch them. Is there some sort of sensor or swith that might be malfunctioning and how can I test it? I have some electrical testing equipment. Thanks.......Guy
Check out the fan switch on the unit and make sure that its the correct one. it should cycloe on @ 120 degrees and cycle off around 100 degrees. Someone may have put in a different one and that is not the approve one.
Posted on Dec 23, 2008
Tips for a great answer:
Jun 25, 2015 | Intertherm Air Conditioners
Jan 06, 2015 | Intertherm Air Conditioners
Feb 15, 2014 | Intertherm P3RA-048K Air Conditioner
Oct 24, 2013 | Coleman Intertherm Nordyne Miller Furnace...
Nov 08, 2011 | Intertherm P3RA-048K Air Conditioner
Nov 12, 2010 | Intertherm Air Conditioners
Oct 20, 2009 | Intertherm P3RA-048K Air Conditioner
Apr 05, 2009 | Intertherm P3RA-048K Air Conditioner
317 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: