The "Aux HT" indicator went on, however the room temp will not go up.
I change the mode to "EHEAT", the fan on the outside unit stopped, "Aux HT" indicator is still on, however the room temp still not goes up. The air comes out of the vent is warm but not hot...
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
I assume that you have a heat pump system. If this is the case, the outside temperature is probably lower than the heat pump is sized for and it is using the auxiliary heating system to keep up. The auxiliary heating system usually is an electric coil in the heat pump unit which supplements the heat being produced by the heat pump. This is normal operations and does not indicate a problem with the heat pump, it is just really cold outside. If it is not colder than usual outside, there may be a problem with the heat pump and you should call a heating contractor to check it out.
If the compressor is running in heat mode but not producing any heat then the change over valve may be stuck. That is a job for a pro. If the thermostat isn't applying power to the changeover valve then a thermostat change is easy to do.
See if it happens only when your temperature of the room is more than 3 degrees of your setpoint temperature. Since you have a heat pump, the auxiliary (electric heat strips) is use for backup of the heat pump when it can't keep up. The heat pump will run by itself if it can maintain temperature within a couple degrees. If it is too cold outside to handle the load or you set the temperature more than 2 degrees past room temperature, the auxiliary will turn on. The thermostat has a memory of how long it takes to reach desired temperature. If it goes into auxiliary mode trying to satisfy setpoint during the last call for heat, it will start the next call for heat in both aux & heat pump mode until the thermostats algorithm (timed program) allows only the heat pump to run. Not sure if you have an air to air, or geothermal heat pump. The outside air temperature will affect only the air to air system ie. when the temps drop outside, the heat coming out of your vents will be cooler...the air to air systems drops efficiency when the outdoor air drops.
Tried this on my unit today, and observed the same results, but got Aux Heat (with A setting), if the H (blue wire) connected to B terminal, as per instructions for my 6036 Ritetemp. However, in this case, when the set temp is reached, I hear the click, but HVAC still blows aux heat indefinitely.
I also have RUUD UBEA 17J10..., and replaced my old honeywell with 6036, and can't get heat pump working. Both of my units are 14 years old, so I'm thinking to replace them soon.
The aux switch is for electric heat banks installed in the air handler. Depending on the outside temp. it may not be efficient to run in heat pump mode but in aux. or emergency would run the electric heat in the air handler.
I think you probably have a heat pump. Aux heat is electrical resistance heat coils that produce heat when the heat pump can not produce enough to keep the temperature up (caused by low outside temperature or a problem with the refrigerant system). This resistance heat can be switched on by the emerg. heat button. It also can come on automaticlly (sp) and will be indicated by the aux being shown on the thermostat. Sometime if you set the heat up several degrees by thermostat the aux will come on to help the system catch up to the desired temperature setting. The emerg. heat is a way to turn on the AUX manually. If you do not have a heat pump system then it is possible that you have a heat pump thermostat installed on a non heat pump system. Emergency heat and Aux are both the secondary.
you need to go oside and look for a red reset button on the unit. you tripped the high ressure switch when you let your filter get that dirty. go check on this and when your done if it still is not working then ask me more.