Question about Heating & Cooling
Propane gas is flowing but, the heater won't ignite.
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Larry, based on the description you have a bad heat limit switch or bad thermocouple. If you want to repair yourself, I can email a document that will assist you in troubleshooting the issue. emial me at email@example.com.
Posted on Jan 10, 2009
SOURCE: Pool Heater
You can light the pilot with a B.B.Q. lighter.
Nottoohandy. Backwash you filter, make sure it's really clean. If that doesn't work it could be the pressure switch. You can by-pass the switch with a piece of wire to see if it fires up. If it does, it's the switch. There is a picture of the switch in the manual.
Posted on May 26, 2008
There are basically three things that can go wrong with the Warm Morning .
Sensor shut off. There is a sensor button on the back of the unit with a wire going from it to the thermocouple. This sensor turns the heater off if the flue is blocked, however it will also shut the heater off if the wire contacts are dirty, or if the sensor has gone bad.
You can test this by bypassing the sensor. Disconnect the two wires from the sensor and reconnect them directly together. If the pilot stays on, your problem is here. Try cleaning the wire contacts first.
Pilot orifice. If the pilot flame is small and doesnt look healthy, the pilot orifice may need cleaning. The hole is very small and can get dirty. Disconnect the silver tube and clean with electrical parts cleaner. Never try to clean the hole with an object like a pin, you may damage it. You may have to slide out the burner unit to get at the silver tube. (Always shut off gas before disconnecting lines and after you reassemble, spray joints with soapywater and look for small bubbles which may indicate a gas leak. Dont use parts cleaner around an open flame.)
Thermocouple can go bad but this is not as common as the first two problems.
Posted on Jan 28, 2010
Is there a frost line on your LP tank, if so you may need to replace the tank with a larger tank or refill your tank. This can happen if the tank your using is too low or too small (use 100 lb tank or greater). If there is no frost line it may be an issue with the thermocouple. The manufacturer offers a service manual and owner's manuals on there site. This should assist you... www.desatech.com Thank you
Posted on Jan 28, 2010
you have to hold for 30 secs to minute once flame is lit if it is like more gas ignition systems
Posted on Feb 09, 2010
Testimonial: "Thanks very much for your useful insight! I thought this might be the problem, but I wanted an expert's advise before I attempted anything like this."
Tips for a great answer:
Jan 26, 2016 | Water Water Heaters
Jul 12, 2014 | Hayward H Series Pool & Spa Heater 400k...
Mar 28, 2013 | Rheem M206A 206K BTU Pool and Spa Propane...
Jan 21, 2013 | Napoleon 36" Zero Clearance Top/Rear Vent...
Dec 22, 2012 | Jandy Laars LX Pool Heater / 250,000 BTU /...
May 28, 2012 | Hayward H Series Pool & Spa Heater 400k...
Dec 10, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Apr 21, 2011 | DCS PHFS Phoenix III Outdoor Patio Heater
Apr 07, 2011 | Hayward 100kbtu Pool Or Spa Propane Gas...
395 people viewed this question
Usually answered in minutes!