Question about Reddy Heater-170,000 BTU Kerosene Deluxe
170 K model, a black wire exits the motor runs through a capacitor I think, then back into motor/pump. The device says CBB20, 370 VAC, 50/60 Hz and Max Temp 90c. One end of the capacitor looks to be melted with gray colored bubbles. Why would this happen and do I just replace it with a new one?
I would replace that and the high heat limit control, it deffinitly got to hot.
Posted on Jan 23, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2017 | Blue Flame Heating & Cooling
Jan 09, 2017 | Heating & Cooling
Jan 05, 2017 | Mitsubishi Heating & Cooling
Jan 05, 2017 | Reddy Heating & Cooling
Jan 04, 2017 | All-Pro Heating & Cooling
Jan 03, 2017 | Heating & Cooling
Dec 28, 2016 | Heating & Cooling
Dec 27, 2014 | Heating & Cooling
Nov 11, 2014 | Heating & Cooling
Nov 28, 2013 | Heating & Cooling
169 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: