Question about Intertherm P3RA-048K Air Conditioner
I came home this morning and the system was blowing cold air... Thermostat set on 68 degrees... The breaker in the panel was tripped. It was around 16 degrees overnight here. Never had any problems until now. The breaker is very warm, but hasn't tripped as of yet.. been on and running for about 2 hours.( Bad breaker, heating coil, ?????)
First, how old is that breaker and are the connections all clean and tight? A warm breaker is normal. If it hot or buzzing, that is another story. If the breaker is more than a few years old, it may pay to invest in a new one. They do wear. If you have a connection which has come loose or is corroded, it will trip the breaker, arc at a connection point or even cause a coil to fail. Dirty connections heat up and actually back off the holding bolts to the point of failure or to tripping the breaker with arcing. With the breaker off, inspect all connections from the panel to the unit. You may get some surprises.
If none of this turns up a problem, inspect the actual heater coil, you may find dirt in there which is causing a problem or the unit itself is failing and touching a grounding point.
Posted on Dec 22, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Heating & Cooling
Feb 18, 2015 | Heating & Cooling
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Feb 09, 2011 | Heating & Cooling
Aug 30, 2010 | Heating & Cooling
Sep 09, 2009 | Ruud Heating & Cooling
Apr 15, 2009 | Heating & Cooling
Mar 23, 2009 | Intertherm P3RA-048K Air Conditioner
Jan 16, 2009 | Heating & Cooling
Nov 29, 2008 | Heating & Cooling
229 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: