Question about Heating & Cooling
You must be having some very cold weather. Heat pumps shut the fan off when the temp. of the coils on the outside hit a certain temperature. That is to increase the pressure inside the unit to get more heat out of it. Your unit also goes into a defrost when ever it gets that cold also. But the compressor turns off also.
Now if your fan never comes on need to check the motor with a ohm meter. And check the capacitor it is a dual one meaning fan and compressor. One side can be out so need to check that also. Turn power off to the outside unit just pull the safety disconnect on the side of the house. Take the capacitor out ohm out the C side and the fan side. You will notice the Herm side meaning compressor. My guess is motor is bad. But I'm not there so concentrate your efforts there. Let me know how it goes okay. Ken
Posted on Dec 21, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 18, 2017 | Carrier Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Mar 26, 2016 | Refrigerators
Nov 01, 2015 | Heating & Cooling
Jul 19, 2012 | Carrier Heating & Cooling
May 20, 2012 | Samsung Refrigerators
Feb 17, 2011 | Heating & Cooling
Jan 21, 2011 | Carrier Heating & Cooling
Jan 12, 2010 | Carrier 38CKC042 Air Conditioner
Sep 17, 2009 | Kenmore 53642 / 53644 Side by Side...
May 23, 2018 | Coleman Heating & Cooling
134 people viewed this question
Usually answered in minutes!