Question about Heating & Cooling
Flame sensor could be dirty. It is located right beside the last burner looks like a thick piece of wire. Take steel wool and gently clean the probe 4 or 5 strokes is all it will take to take off the carbon build up off. Lets eliminate this item and see if it clears up okay. ken
Posted on Dec 21, 2008
Posted on Dec 02, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: armstrong ultra sx 80 furnace
You have a dirty flame sensor. Look at the very last burner and you will see a wire going to a ceramic sensor and it looks like a thick wire. Take some steel wool or fine sandpaper and clean the surface off and it will work like a champ.
Let me know how it goes ken
Posted on Apr 15, 2009
Tips for a great answer:
Jan 08, 2017 | Heating & Cooling
Oct 04, 2015 | Heating & Cooling
Oct 03, 2015 | Armstrong Cars & Trucks
Oct 19, 2013 | Emerson Lennox Ducane Armstrong Furnace...
Oct 18, 2010 | Honeywell Heating & Cooling
Sep 26, 2010 | Heating & Cooling
Jan 10, 2010 | Armstrong H 67 1PH Bf In Line Circulator...
Apr 15, 2009 | Heating & Cooling
Sep 25, 2018 | Heating & Cooling
2,004 people viewed this question
Usually answered in minutes!