Question about Amana PTH123B25AJ Heat Pump Air Conditioner
We have had this unit for almost 8 years and have had no problems. My wife turned on the unit and heard a pop and now it wil not come on. I have checked the breaker and the fuse and they are ok. What do I need to check next? Any help would be gratly appreciated. Thanks
The relays in these units blow, hence the popping noise you heard, disconnect power and remove the electronic control board. Flip it over and look under the relays, you will see burn marks under the one that blew. You can order a new board from Amana for around $130.
Posted on Feb 10, 2009
Its apretty straight foward thing(usually).. there is a power board that controls the uint, so long as you have power in to the unit this is where the problem lies, replacing the circuit board will problably due the trick
Posted on Dec 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 21, 2015 | Amana Heating & Cooling
Dec 28, 2014 | Amana PTC153B35AJ Air Conditioner
Sep 03, 2014 | Amana PTC124E50AXXX
Feb 14, 2013 | Amana PTC093B50AJ Electric Heat Air...
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
May 14, 2011 | Amana PTH123B25AJ Heat Pump Air...
Jun 19, 2010 | Amana PTH093B35AM Thru-Wall/Window Air...
Jan 28, 2010 | Heating & Cooling
Jul 23, 2009 | Amana PTH123B25AM Air Conditioner
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
710 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: