Question about LG LW1200ER Air Conditioner
Any ideas? There is air blowing through the vents, but it isn't hot!! Please help!!
These new furnaces are trouble. Ive been in the htg trade for 25 yrs. The fan is running because they are now controlled by a timer instead of a temperature control. Rather than sensing a preset temperature and turning on the fan, it comes on by a preset time. Couple of things, does either of the doors have an inspection window? most newer furnaces have what is called a smart board. The board will flash a trouble code. ie: 1 long 2 short etc. #1 turn your thermostat to off, youll need 2 people for this! Go to the furnace, If it has the above mentioned inspection window ( usually about 2" round) while peering through the window have someone turn the thermostat to about 80 degrees. Let the furnace cycle and see if it flashes a code. If it does the codes are usually on the bottom door, May be on the inside. The most common cause is either a bad transformer, bad hot surface ignitor or pressure switch failure. Further questions feel free to ask. Steve
Posted on Dec 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 08, 2017 | Amcor Heating & Cooling
Jan 08, 2017 | Coleman Heating & Cooling
Jan 07, 2017 | Heating & Cooling
Jan 03, 2017 | Royal Heating & Cooling
Dec 31, 2016 | Heating & Cooling
Dec 18, 2016 | Heating & Cooling
Dec 25, 2014 | Heating & Cooling
Oct 28, 2012 | Heating & Cooling
709 people viewed this question
Usually answered in minutes!