Question about Heating & Cooling
I have the same issue - and I posted this on the original thread someone else posted.
*** I had issues determining what color the "common" wire was. I have ared, white, yellow and green. Between the white and red i get .10-.70volts - between the yellow or green and red I get 28 volts.
Sodoes this mean I need better batteries - the instructions say"energizer" - but if this is the case - does it mean it is not myfurnace?
I can hear the unit buzzing atop the roof. But insideto air blows unless I turn the "fan" position to "on". - Then of courseno heat comes out.
Would be grateful for any reply!
Typically red is power green is indoor fan white is for heat and yellow is for cooling. Sounds like you don't have a common. This IS ok just means your tstat requires batteries. BUT, if your tstat turns the fan on then it's not the batteries. Is this a newly installed tstat? Sounds like you might be on "gas" setting rather than "electric" need to check the settings or sometimes on the back of the tstat there's a little switch to flip to electric. Many tstats come from the manufacture set for gas rather than electric. Good Luck!!
If you need further help, reach me via phone at https://www.6ya.com/expert/thomas_092728000e6acb79
Posted on Apr 05, 2017
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Thanks for the response, to be more specific, the nine pin connector was damaged, but I was able to connect the wires back to main unit panel. I am ready to hook to the hunter thermostat and do not know which wires to connect to. This is my problem and I do not want to short something out. Hope this helps, I want to get it installed again. Thanks again for caring....Jerry
Posted on Aug 16, 2008
/* Style Definitions */
mso-padding-alt:0in 5.4pt 0in 5.4pt;
font-family:"Times New Roman";}
Thermostat wire color codes
Please note. Not all installers use the proper color codes when they install or replace equipment. It may be necessary go go to the furnace or outdoor unit to verify what wires are for what purpose. Also be sure there are no splices in the wire that could change the wire colors between components.
Posted on May 07, 2009
SOURCE: Thermostat Wiring Problems!!!
. your blue is probably common and if you hooked it to Y you shorted the transformer or blew the low voltage fuse. Green is fan, yellow is AC, Red is 24volt. Is it a heatpump or just ac? I think its probably a heat pump and your brown is your Reversing valve it needs to be hooked to O on the new stat. If its a heatpump your tstat must be a 2heat 1 cool stat w/ aux heat. Without knowing what terminals the wire were hooked to on the old stat you may have to look at whats hooked up at airhandler( furnace) and on A/C (heatpump) tobe able to determine what goes where on the new one.
Posted on Sep 20, 2009
Testimonial: "Thank you, it was a heat pump"
If the Air comeing out is the same as the temp inside the RV make sure the compressor is running and not just the fans. It could be low on freon. If freon is ok then you would need to ck the wiring to the selector switch for a short. It would be obviouse because there will be melted wires. I am leaning toword low on freon since you have already been inside the wiring/control unit.
Posted on Aug 08, 2010
Tips for a great answer:
Aug 16, 2018 | Honeywell Heating & Cooling
Jun 12, 2007 | White Sewing Speedylock 1600 Mechanical...
Sep 03, 2015 | Cars & Trucks
Apr 17, 2015 | Heating & Cooling
Jul 06, 2012 | Toshiba 42HM66 42" Projection HDTV
Jun 16, 2010 | Shaw Robert RS-9420 Thermostat
Feb 24, 2010 | Shaw Robert RS-9420 Thermostat
Feb 04, 2010 | Shaw Robert RS-9420 Thermostat
Jan 08, 2010 | Carrier 38CKC036 Air Conditioner
86 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: