Question about Goodman CLQ36AR49 Air Conditioner
I have a 4 year old 5 ton goodman heat pump.The breaker for the outside unit jumped to the off position. I have no power even the thermostat is off. The repair guy came replaced the Inside fan motor,everything was good for about six hours .Now its off again the exact same problem? Please Help.
Sound like the outside unit is going to ground or the unit is over amping. Take and shut off the power to the unit and check all of the electrical connection for tightness. Don't forget to check the disconnect wires too since you shut it off at the breaker box. If you have a meter check to see if it''s live before you work on it. If it's all tight then call back the person that did the previous repair and tell them that he obviously missed something and the you feel that it should be a warranty call.
Posted on Dec 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 18, 2015 | Goodman Manufacturing Goodman GPH1330M41...
Oct 13, 2014 | Heating & Cooling
Mar 25, 2014 | Goodman Heating & Cooling
Aug 17, 2012 | Goodman Heating & Cooling
Jul 12, 2010 | Goodman CKL36AR36 Air Conditioner
May 20, 2010 | Goodman CLQ36AR49 Air Conditioner
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 04, 2009 | Goodman CLQ36AR49 Air Conditioner
118 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: