I have a 4 year old 5 ton goodman heat pump.The breaker for the outside unit jumped to the off position. I have no power even the thermostat is off. The repair guy came replaced the Inside fan motor,everything was good for about six hours .Now its off again the exact same problem? Please Help.
An expert who has achieved level 3 by getting 1000 points
An expert that got 10 achievements.
An expert that got 5 achievements.
An expert whose answer got voted for 100 times.
Re: goodman heat pump 5 ton power problem
Sound like the outside unit is going to ground or the unit is over amping. Take and shut off the power to the unit and check all of the electrical connection for tightness. Don't forget to check the disconnect wires too since you shut it off at the breaker box. If you have a meter check to see if it''s live before you work on it. If it's all tight then call back the person that did the previous repair and tell them that he obviously missed something and the you feel that it should be a warranty call.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Seriously depends on what unit you have. Model # & serial #? You can "jump" R to G at the unit. If its a standard Goodman AHU there may be a terminal block or just some wires that were factory installed outside of the unit. R to G will send 24v to the blower relay, sequencer or board (depending on model) energizing the relay and then returning to common. If you have tried that you should ensure you have proper line voltage 220-240vac. at the service breakers on the AHU.
Im assuming you mean the low voltage fuse? In that case its located on the circuit board inside the electrical panel on the unit. If looking for the high voltage fuse (breaker) you should have a disconnect outside protected by a breaker inside at the electric service panel (breaker box).
first confirm that the condensing unit outside is getting power or even a command to come on .check function of thermostat your t-stat may command heat in the cooling mode.instead of the heat mode, being a heating system generated by a cooling condensor. also check bateries in t-stat. make sure breker in the panel box is on ,it is a double breaker usualy marked with an amp rating of 20 ,or a 30 on it . also check disconnect switch located next to your outdoor condensor usualy a gray box on wall of building. make sure its on or diconnect tab is pluged in . hope this was helpful. good luck.
Your going to need to know the age of the unit. If its less than 5 years old, its most likely a 13 SEER. If its anything more than 5 years old, its most likely a 10 SEER. If its anything over 10 years old, its most likely an 8 or 6 SEER.
Remember, that a unit will loose an average of 1-2 SEER for every full year of operation. This is just due to age, wear and tear, and usage.
So, if its a 10 SEER unit that is 7 years old, you could say that it is about as efficient as something in the 4-6 SEER range.
Easy: Turn the "fan" switch to on at the thermostat and see if the blower starts. If no start, check breaker at breaker box. Check service disconnect at or near the air handler. With the breaker and/or service disconnect OFF check the 3 or 5 amp fuse inside the top cover in the air handler. Not so easy: (You must know what you are doing for this part or let an HVAC Tech do it for you) Open thermostat and firmly jump the Y and R terminals to see if you get the compressor to start for no more than 30 seconds. (don't do it more than once.) Jump the G and R terminals to see if you get the blower to start. If so, u have a bad thermostat. If not, check the transformer inside the same cover in air handler for proper voltage. (24V. Make sure you also get 220 on the opposite side of the transformer) If the blower comes on, but the heat pump doesnt start, open the side cover of the heat pump, with the thermostat on cool, and the temp. setting as low as possible for at least 10 minutes see if the contactor is pulled in. If so, check the capacitor and see if it's blown out. Be super careful these systems operate with 220v and the amperes are enough to kill you if you make a simple mistake.
That does not sound normal at all, I have a Goodman Heatpump and the Fan on the Evaporator (outside unit) should run as soon as it starts up! The only delay you should be seeing is when the unit starts, the fan in the AHU starts 5 seconds after and runs for about 1.5 minutes after shutdown.
First of all is this unit a heat pump i'm not up on goodman model #'s if it is a heat pump reversing valves do go not a real common problem 1000.00 is excessive i would be inclined to get a 2nd opinion. plastic over the sand could create a condensation mold problem. Good luck. Tom
this is a 3 ton unit it still has parts warranty on it if you look inside the fan area of out door unit the reversing valve has 3 copper lines on one side and 1 on the other fyi when giving call for cooling out door fan running? if no check for fuses in disconnect at unit or breaker off in panel remove panel where power comes to unit pull disconnect look at capacitor silver thing with wires on top if swollen on top bad hope this helps some