Range master toledo 90
I would follow these requirements if I were you:
The cooker must be connected to the correct electrical supply as stated on the voltage label on the cooker (This is obvious so far!). It should be connected through a suitable cooker control unit incorporating a double pole switch having a contact separation of at least 3mm in all poles (This means one of those big red switches with "COOKER" written on them). The cooker must NOT be connected to an ordinary domestic power point. The cable size used should be between 6mm squared and 10mm squared twin and earth. Where the installation is protected by a 30 milliamp sensitivity residual current device (RCD Breaker), the combined use of your cooker and other domestic appliances may occasionally cause nuisance tripping. In these instances, the cooker circuit may need to be protected by fitting a 100 milliamp device. This work should be carried out by a qualified electrician.
Oct 28, 2007 |
Rangemaster Toledo 90 (Dual Fuel) Dual...