Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
The heater works just fine, heats well. CO detectors (nightHawk Digital) all read 0ppm. Noticed a pungent odor outside when heat is on and there is a brown coating on aluminum exhaust vent tube. This tells me the gas may not be burning completely and perhaps increasing my heating bills. I want to open the unit to check for air inlet restrictions & clean whatever may be dirty & interfering with the air/gas mixture.
The gas pack is beside the house and easy to access, top comes off easily.
Looking for pointers on what to expect & procedures for this service.?
Time for a good cleaning. Make sure the heat exchanger is in good shape and is getting good heat flow over it to the exhaust. The odor may be an indication of a restriction in the heat exchanger, the flames are hitting something, improper air or gas adjustment or a blower not coming up to correct speed. You can access the heating unit from a side panel. Look for the exhaust port and start with that panel. Wasps nests are predominant in these things.
Posted on Dec 19, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 08, 2014 | Water Heaters
Oct 31, 2011 | Goodman GMS90703BXA Heater
Jan 30, 2011 | Kidde Nighthawk Combo Gas/co Detector
Nov 20, 2010 | Kidde Nighthawk Combo Gas/co Detector
Oct 18, 2010 | Kidde Nighthawk Combo Gas/co Detector
May 17, 2010 | Kidde Nighthawk Combo Gas/co Detector
Apr 03, 2010 | Kidde Nighthawk Combo Gas/co Detector
Mar 08, 2010 | Kidde Nighthawk Combo Gas/co Detector
Apr 22, 2009 | Kidde Nighthawk Combo Gas/co Detector
Dec 16, 2008 | Kidde Nighthawk Combo Gas/co Detector
666 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: