Question about Kitchen Appliances - Others
I try to turn on my furnace and i get a flashing code
furnace wont turn on / pressure switch stuck open what should i do
Check the intake and exhaust plumbing for any obstructions. I had same issue, turned out to be ice in the air intake plumbing on outside of house. This may be the problem. The pressure switch can be tested by pulling hose from purge motor that goes to switch and applying a small amount of suction. The switch should make a clicking sound.
Posted on Jan 20, 2009
3 Flashes means pressure switch malfunction......had the same 3 flashes and when i changed the pressure switch all was well and good.
Posted on Jan 15, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 23, 2016 | Heating & Cooling
Nov 28, 2015 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Oct 28, 2011 | Goodman Heating & Cooling
EACH OF THE FOLLOWING STATUS CODES IS A TWO DIGIT NUMBER WITH THE FIRST DIGIT DETERMINED BY THE
NUMBER OF SHORT FLASHES AND THE SECOND DIGIT BY THE NUMBER OF LONG FLASHES.
43 LOW-HEAT PRESSURE SWITCH OPEN WHILE MEDIUM-HEAT PRESSURE SWITCH IS CLOSED - Check for:
- Low inlet gas pressure (if LGPS used).
- Plugged condensate drain.
- Improper pressure switch wiring.
- Water in vent piping, possible sagging pipe.
- Stuck open low-heat pressure switch.
- Disconnected or obstructed pressure tubing.
Mar 28, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 04, 2011 | Goodman GMS90703BXA Heater
Dec 12, 2009 | Heating & Cooling
Nov 16, 2009 | Coleman Propane Forced Air Heater...
8,836 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: