Question about Goodman CLQ36AR49 Air Conditioner
I have an R410 Goodman heatpump. It works just fine in AC mode. 300 on high side and 105 on low with 70 degrees outside. When I try to turn on the heat pressure on BOTH sides goes beyond 600 and then overload protection kicks in and compressor shuts off. Is it a bad reversing valve? Heat pump is only 6 months old.
Check the TXV valve on the outdoor unit, it could be stuck closed. We have been experiencing the same problems with the 410 systems and the TXV was the culprit. Good Luck
Posted on Feb 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 20, 2014 | Heating & Cooling
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Aug 03, 2011 | Goodman CKL30AR30 Air Conditioner
Aug 01, 2011 | Goodman CKL30AR30 Air Conditioner
Jul 15, 2011 | Heating & Cooling
Jun 07, 2011 | Amana Heating & Cooling
Nov 01, 2010 | Heating & Cooling
Feb 15, 2010 | Heating & Cooling
Nov 21, 2009 | Humidifiers
Apr 19, 2009 | Ruud UBHC Air Conditioner
522 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: