Question about Goodman CLQ36AR49 Air Conditioner
I have an R410 Goodman heatpump. It works just fine in AC mode. 300 on high side and 105 on low with 70 degrees outside. When I try to turn on the heat pressure on BOTH sides goes beyond 600 and then overload protection kicks in and compressor shuts off. Is it a bad reversing valve? Heat pump is only 6 months old.
Check the TXV valve on the outdoor unit, it could be stuck closed. We have been experiencing the same problems with the 410 systems and the TXV was the culprit. Good Luck
Posted on Feb 10, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 20, 2014 | Goodman CLQ36AR49 Air Conditioner
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Aug 01, 2011 | Goodman CKL30AR30 Air Conditioner
Jul 15, 2011 | Heating & Cooling
Jun 07, 2011 | Amana Heating & Cooling
Aug 16, 2010 | Goodman Heating & Cooling
Aug 09, 2010 | Goodman CLQ36AR49 Air Conditioner
Feb 15, 2010 | Heating & Cooling
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Sep 07, 2008 | Goodman CLQ36AR49 Air Conditioner
531 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: