Hi, My spaceheater will run for a couple of hours then flashes both front panel indicator lights red, indicating air-filter cleaning required. But the filters arevery clean. Turning off the economy mode alleviates the problem, but thats not suitable for constant running. No error codes appear.
An expert who has achieved level 3 by getting 1000 points
An expert that got 20 achievements.
An expert that got 10 achievements.
An expert that got 5 achievements.
Re: Rinnai Energysaver 1004FTR (nat gas) RED FLASHES
The filter light can also indicate a build up of debris and lind behind the heater causing the blower to work harder to push out warm air. It could also indicate that the blower may need a cleaning or going bad. I will suggest that you pull the front cover off of the unit to inspect the blower which is located at the top of the heater. Feel the motor as it is running to see if it is hot. If so, you will probably need to replace it. I may have a used on so let me know. If everything in front looks good, pull the top trim panel off of the heater just behind the filters and inspect for dust. Clean with a shop vac. Hope this helps.
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US. click here to Talk to a Repairman (only for users in the US for now) and get all the help you need. Goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Two things- Clean the sensor rods or replace(cheap and easy with YouTube instruction video) and at the same time replace the main program chip (also a easy plug in chip). The whole repair takes two hours for a homeowner and costs about 50 bucks for a chip. These are easy an generally the flame sensor rod is the culprit. The code may also be the limit switch but try EZ and cheap first. See You Tube..
Check the pressure reading, should be about 1 bar when system is cold. Various models in the range of 24cdi. If you do not have a manual, go to, http://www.centralheating.co.uk/Boiler-Manuals/worcester-bosch-boiler-manuals/worcester-bosch-discontinued-boiler-manuals. Get the manual for your unit, to wards the end of install manual it has a fault finder, Also has a basic 1 in the user manual. Number of flashes how fast the light flashes which one flashing can all mean different, So get the manual and check, Some parts are easy to fix, as long as you do not touch the gas side the rest is plumbing. Come back if needed.
Attached to the water heater is a troubleshooting chart for your sequence light. 1 flash means..., 2 flashes means...., and so forth. Find the chart, count the flashes and see what it means and we'll go from there. Douglas
A 20 error code means the high limit switch is being tripped. This is most typically caused when scale develops in the heat exchanger. I'd recommend performing a descale on the heater to resolve the problem. Make sure to follow the instructions that came with your isolator valve kit.
first find out from your manual what the flashing red light means...that should narrow your search---could be a thermocouple shot,a rubber diphragm in the gas valve has weakened and not operated, or gas pressure into the appliance may suddenly be too low, or springs in gas valve may have worn out---very many possibilities
Pressure is ok? at 1 bar or above I think on this one there should be a reset button [red] on the left hand top of the casing - or lower the control panel [ phillips screw on each side] and the button is on the left of the base plate. Press this and try the heating.or hot tap P.S. if you're on a prepayment meter check you have gas.
1.Not an expert with natural gas furnaces. 2.Statements below are from my own personal experience, and knowledge from.
The red blinking light you see is on a computer control board. The flashes of the red light represent a type of code. Think of it as a Morse Code, if you will.
For example: Red light blinks three times rapidly, pause, then blinks one more time. This code represents a particular fault. (Fault = Problem)
There is a sticker, with a chart of codes listed for this red light. It is usually placed very near the red light.
A gas furnace should be repaired by a competent HVAC technician. This is not a device that should be attended to, by those who are not trained. An HVAC technician will know where to look, what parts are needed, and if the gas furnace is safe enough to put back on line. (Safe enough to use)