Question about Heating & Cooling
There should be electric heat strips in the airhandler.
They automatically come on when the unit goes into defrost, the thermostat is turned up more than 7 degrees over the indoor temp or if the outdoor temp is just so cold the HP cannot keep up.
Tat is your auxillary or emergency heat.
What does the new t-stats installers booklet say that the 0170 function and #2 #7 options are for?
If it is for gas vs elec heat then set it on the elec option.
The difference is that in gas heat systems the blower comes on a few min AFTER the furnace fires up to allow the heat exchanger to get hot.
In an electric furnace the blower has to come on emediatly because the heat strips get hot emediatly and if the blower is delayed the system will shut of in high temp overload.
Posted on Dec 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 17, 2016 | Toys
Jan 31, 2011 | Goodman CKL60AR60 Air Conditioner
Sep 03, 2010 | Dometic Rooftop RV Air Conditioner
Jan 30, 2010 | Heating & Cooling
Dec 29, 2009 | Honeywell Electronic Programmable...
May 29, 2009 | Honeywell Electronic Programmable...
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Sep 30, 2008 | Heating & Cooling
353 people viewed this question
Usually answered in minutes!