Question about Air Conditioners
There should be electric heat strips in the airhandler.
They automatically come on when the unit goes into defrost, the thermostat is turned up more than 7 degrees over the indoor temp or if the outdoor temp is just so cold the HP cannot keep up.
Tat is your auxillary or emergency heat.
What does the new t-stats installers booklet say that the 0170 function and #2 #7 options are for?
If it is for gas vs elec heat then set it on the elec option.
The difference is that in gas heat systems the blower comes on a few min AFTER the furnace fires up to allow the heat exchanger to get hot.
In an electric furnace the blower has to come on emediatly because the heat strips get hot emediatly and if the blower is delayed the system will shut of in high temp overload.
Posted on Dec 18, 2008
Tips for a great answer:
Feb 27, 2015 | Air Conditioners
Nov 05, 2014 | Honeywell VisionPRO 8000 Programmable...
Jan 31, 2011 | Goodman CKL60AR60 Air Conditioner
Sep 03, 2010 | Dometic Rooftop RV Air Conditioner
Oct 30, 2009 | Weather King 10AJA6001AH Air Conditioner
Sep 20, 2009 | Air Conditioners
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Sep 30, 2008 | Air Conditioners
May 17, 2008 | Honeywell Air Conditioners
Dec 08, 2016 | Amana Air Conditioners
353 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: