Question about Ruud UAKA042 Air Conditioner
I have a RUUD upka-042JAZ heat pump. I noticed a problem in the winter, when it was not getting warm enough. A technician determined the outside unit (i'm assuming heat) was not coming on as it should. The heating elements within the inside unit were the only thing working. He also mentioned that I had the wrong thermotstat which was for a conventional AC and not a heat pump. He replaced the thermostat but the outside unit still did not come on. Winter was not that extreme last season so it really was not a problem. Because low and behold he never showed up again to finish the job. Now its summer and the unit outside does not come on. The pipes to the outside unit are normal air tempurature. (i'm assuming they should be hot) Anyway before he worked on it to fix the heat I know for a fact the outside unit was working. It may be just coincidence but not sure. Anyway the inside unit does come on but i suspect its just the blower because the air is room tempurature and not cold. Technician around here are hard to find. I think its part of the katrina rebound. I've also noticed a reset button on the outside unit (not sure what it does though). I have powered down everything (breakers) and pressed the reset button thinking that this might help. no luck though. Anyway thanks Dave
YOUR MODEL HAS A 3-5 MIN.TIME DELAY RELAY IN THE CONDENSER CONTROL PANEL OUT-SIDE. DO NOT ATTEMPT TO FIX-IT YOURSELF ... THERE I SAID IT. IT IS WIRED INTO THE 24VOLT CONTROL CIRCUIT. THEY DO GO BAD AND OFTEN. IT IS THERE FOR A GOOD REASON. IT GIVES THE COMPRESSOR TIME FOR THE PRESSURES TO EQUALIZE INTERNALLY TO PREVENT "HARD START CONDITIONS". RUUD HAS A GOOD WARRANTY ON ALL PARTS 5-6 YEARS I BELIEVE. IF IT IS THE TIMER IT IS INEXPENSIVE ANYWAY. GOOD LUCK
Posted on Apr 27, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 27, 2011 | Heating & Cooling
Jan 28, 2011 | Ruud UAKA042 Air Conditioner
Jan 17, 2010 | Ruud Matching Split Air Conditioner
Jan 03, 2010 | Heating & Cooling
Jun 17, 2009 | Ruud UBHC Air Conditioner
Jun 01, 2009 | Ruud UAMB Air Conditioner
Feb 13, 2009 | Ruud UBHC Air Conditioner
Nov 17, 2008 | Ruud Heating & Cooling
Jan 15, 2008 | Ruud UAKA042 Air Conditioner
Oct 27, 2007 | Ruud UBHC Air Conditioner
Sep 01, 2013 | Ruud UAKA042 Air Conditioner
338 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: