Question about Dyna-Glo D-E37 Wall Mounted Panel Heater
I have a new dyna glo heater, and it will light and run fine for a period of time (time varies) before it simply shuts off. After doing this intermittently for the past 48 hours, the smaller bathroom heater is experiencing the same issues. HELP
Lp or natural gas sounds like moisture in the line look for a trap should look like a tee with a cap on it turn off gas and remove cap and see if any moisture in line replace cap and turn on gas check for leaks with soapy water and a small brush if not moisture it could also be air in line if so it will bleed itself out in a little while and work normally
Posted on Dec 17, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2016 | Dyna-Glo Heating & Cooling
Jan 12, 2016 | Heating & Cooling
Dec 31, 2014 | Dyna-Glo Dyna Glo Delux 650,000 BTU...
Mar 06, 2011 | Dyna-Glo Heating & Cooling
Jan 31, 2011 | Dyna-Glo RMC-8001SS Heater
Dec 17, 2009 | Dyna-Glo RMC-8001SS Heater
Oct 08, 2009 | Heating & Cooling
Feb 03, 2008 | Dyna-Glo (PPH16-LP) Utility Heater
805 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: