Question about Goodman GMS90703BXA Heater
My 3 year old Amana is giving me some serious issues. I have had 5 servicemen over now who haven't been able to fix it. The problem seems to be that after a successful heating, the inducer blower does not turn off. The unit is then unable to fire again. At this point I get the double blink from the control module that translates to "Low fire pressure switch stuck closed" Any Ideas? Help!
Check the condensate drain, hoses and pump if it has one. Like Drumbanger says, check the pressure switch. Also check the intake and exhaust vent for blockage of water or debris. All water should drain back to the furnace and not collect in the venting. Your furnace has two pressure switches, replace the low pressure switch.
Posted on Feb 18, 2009
It sounds to me like the pressure switches need replaced or they need removed and shaken upside down to get the condonsation out of them!Good luck and Thank you for using FixYa.
Posted on Dec 17, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 17, 2015 | Amana Heating & Cooling
Mar 02, 2015 | Heating & Cooling
Mar 03, 2013 | Omega Trane Furnace Draft Inducer Blower...
Feb 15, 2011 | Goodman GMS90703BXA Heater
Jan 10, 2011 | Heating & Cooling
Jan 01, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 07, 2009 | Goodman Furnace Draft Inducer Blower ...
Oct 20, 2009 | Goodman Heating & Cooling
Dec 17, 2008 | Heating & Cooling
466 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: