Pilot ligting instructions
many of the newer furnaces don't have a standing pilot. look to see if you have a gas valve with a knob on top that says off pilot and on. look to see if a tube the size of a pencil comes out of the valve and goes down by one of the burners, look to see if there is a little gold piece of metal tubing protruding down to the opening of the larger tube . that is where you place the match. i prefer to use a grill lighter. safer and positive flame. turn knob to off wait 5 minutes for any gas to disipate. be sure your incoming gas valves are all open . usually at the meter and one at the furnace. usually the handle is in line with the pipe when open. from the off position, turn the knob on the furnace gas valve to pilot position and push down on it as you turn. this lets gas flow to the pilot tube by the burner where you have you flame starter lit and waiting. once pilot lights hold down on button for 3 minutes or less. longer is better to be sure the thermocouple senses flame . then gently release the downward pressure and the pilot should stay lit and you gently turn knob to on. if pilot goes out you may have a bad thermocouple. be especially careful if its lp or propane as that gas does not disipate like natural gas and can virtually lay on the floor till ignited. also consider having the heat exchanger checked by a pro with a carbon monoxide detector. they do crack after a few years and can be deadly when they do. good luck
Nov 13, 2008 |
Carrier XHB123D X/Y Series Heat/Cool Air...