Question about Fahrenheat Electric Convector Baseboard Heater, 240 Volt
How do you know how much footage of baseboard per room. And can all rooms be wired to one thermisate.
HERE YOU GO CALCULATE THE HEAT @ 10 WATTS PER SQUARE FOOT , TAKE THE LENGTH X WIDTH X 10 AND THIS WILL TELL YOU THE AMOUNT OF WATTAGE YOU NEED . MOST ALL BASEBOARD HEATERS ARE RATED @ 250 WATTS PER LEN FT AS TO SAY A EX. A 4FT HEATER IS 1000 WATTS , MOST OF THE THERMOSTATS ARE RATED @ 20 AMPS AS IS THE 12-2-WG WIRE TO RUN TO HEATERS AND THERMOSTAT DIVIDE THE TOTAL WATTAGE BY THE LINE VOLTAGE USUALLY 240VOLT IN US .AND THIS WILL TELL YOU THE CURRENT DRAW ----WHICH CANNOT EXCEED 20 AMPS ON 12-3-WG AND THAT IS THE LIMIT OF THE THERMOSTAT AS WELL THESE STATES APPLY 99% OF THE TIME I DO REALIZE THERE ARE EX BUT HAVE USED THESE FORMULAS FOR 35 YEARS OF DOING MY WORK AND THEY DO FINE
Posted on Dec 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 20, 2017 | Heating & Cooling
Oct 01, 2014 | Honeywell Heating & Cooling
Jan 21, 2011 | Fahrenheat Electric Hydronic Baseboard...
Mar 03, 2010 | Fahrenheat Electric Convector Baseboard...
Oct 16, 2009 | Fahrenheat Electric Convector Baseboard...
Sep 29, 2009 | Fahrenheat Electric Convector Baseboard...
Dec 25, 2008 | Marley Electric Hydronic Baseboard Heater,...
Sep 11, 2008 | Fahrenheat PHH15002 Oil Filled Baseboard...
370 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: