Question about Heating & Cooling
Recheck the wiring on the thermostat and at the package unit to be sure that nobody took and wired them incorretly so that the heat worked.
Posted on Mar 21, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 02, 2018 | Heating & Cooling
Jan 20, 2016 | Gibson Nordyne/2 Ton Heat Pump Package...
Dec 19, 2015 | Rheem 3 Ton 14 Seer Package Heat Pump -...
"PLACE A JUMPER (PIECE OF WIRE) BETWEEN Y AND W IF YOU ARE USING A HEAT PUMP WITHOUT AUXILIARY/BACKUP HEAT." if this dosnt work check the fuse in the air handler you may have blown it if you did not turn the unit off before installing.
Mar 25, 2014 | Goodman Heating & Cooling
Jan 25, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Nov 29, 2013 | Rheem 3.5 Ton 14 Seer / Ruud 100K Btu 80%...
Nov 26, 2013 | American Standard Heating & Cooling
Aug 22, 2011 | Goodman CKL36AR36 Air Conditioner
Jan 07, 2010 | Goodman Heating & Cooling
Jan 30, 2009 | Amana PTH123B25AJ Heat Pump Air...
32 people viewed this question
Usually answered in minutes!