Question about Reddy Heater-30-55,000 BTU Variable
When i plug it in, after tree sec. the fan will turn and fumes will blow out the front of it for three sec. then the fan will stop please help i am cold
Check the seal around the fuel tubes; mine was sucking air around the tube causing blow-out.
Posted on Jan 19, 2013
I had the same problem. I took the nozzle head off and blew through it with air. I also blew through the air line, this is the one that goes to motor. It has worked fine ever since.
Posted on Jan 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2014 | Heating & Cooling
Nov 14, 2011 | Reddy HEATER R115 115,000-BTU PORTABLE...
Nov 10, 2010 | Reddy HEATER R115 115,000-BTU PORTABLE...
Nov 02, 2010 | Reddy HEATER R115 115,000-BTU PORTABLE...
Feb 13, 2010 | Reddy HEATER RLP100 100,000-BTU PORTABLE...
Jan 17, 2010 | Reddy HEATER RLP100 100,000-BTU PORTABLE...
Jan 10, 2010 | Mr. Heater Portable Propane Forced Air...
Jan 02, 2010 | Reddy Heater 60,000 BTU Kerosene...
Jan 13, 2008 | Reddy HEATER RLP100 100,000-BTU PORTABLE...
Dec 06, 2007 | Reddy Heater-30-55,000 BTU Variable
2,118 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: