Question about Aprilaire 600 Humidifier
It is not likely to be caused by the selonoid valve. The selonoid is designed to be either open or closed, so if the unit is calling for humidity, it should be 100% open allowing as much water as possible to flow through. In cases of a bad selonoid, it will usually stick open or stick closed, but I have never heard of one allowing too much water through. Check to make sure your drain is clear and that the incoming line to the humidifier is positioned properly on the inside of the unit. If this doesn't solve the problem, it could be that the water line to the humidifier is too large, allowing more flow than the unit is designed for.
Posted on Dec 16, 2008
Tips for a great answer:
Jan 23, 2015 | Humidifiers
Jan 08, 2010 | Aprilaire 600 Humidifier
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Jan 16, 2009 | Honeywell Power Humidifier: Furnace...
Jan 07, 2009 | Aprilaire 600 Humidifier
Dec 16, 2008 | Aprilaire 600 Humidifier
Feb 16, 2008 | Aprilaire 600 Humidifier
Jan 03, 2008 | Aprilaire 700 Humidifier
Dec 31, 2014 | Aprilaire 600 Humidifier
Dec 19, 2014 | Aprilaire 600 Humidifier
143 people viewed this question
Usually answered in minutes!