Question about Goodman Heating & Cooling
After the gas turns on, it is the flame sensor's job to see that ignition took place and send 24v to the gas valve. If it does not do this, the gas valve shuts down as a safety precaution. After 3 tries, the furnace will go into "lockout" and will not let it attempt to start again. The lockout can be resolved by turning off the power to the furnace for a couple minutes and then turning it back on. Sounds like the real problem is a faulty flame sensor not sending 24v to the gas valve. Sometimes they can be cleaned with a piece of sandcloth. This will cure failure to recognize the flame due to carbon build up on the sensor. Otherwise, the sensor will need to be replaced. Hope this helps!
Posted on Dec 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 20, 2014 | Rheem Richmond 40 Gal Natural Gas 6 Year...
Oct 29, 2013 | Jandy Laars Lt 250,000 Btu Heater
Aug 26, 2011 | Sta Rite Sr200lp Max E Therm Pool & Spa...
Nov 16, 2009 | 1991 Chevrolet Corvette
Oct 03, 2009 | Desa International GWP20T GLOWARM Wall...
May 27, 2009 | Pentair Minimax NT Heater
May 26, 2009 | Jandy Laars LX Pool Heater / 400,000 BTU /...
Jan 24, 2009 | Water Heaters
230 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: