Question about Carrier Heating & Cooling
Posted on Dec 15, 2008
The fan control is the problem and will need to be replaced. First you should check for voltage at the fan. Also will it work manually? If so, then the cheaper option would be to run it manually for now if you don't want to replace the control unit. Let me know what you find. A volt meter can be bought from Radio Shack if you don't have one.
Please post any other questions you may have
Posted on Dec 15, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 12, 2015 | Carrier Heating & Cooling
Nov 03, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 08, 2011 | Whirlpool 16.7 cu. ft. Upright Freezer...
Jun 29, 2011 | Heating & Cooling
Mar 31, 2011 | Kenmore Refrigerators
Dec 18, 2010 | Carrier 38CKC042 Air Conditioner
Here is the reason for that problem per the manufaturers web-site
The low-pressure switch senses the refrigerant pressure in the sealed refrigeration system to
protect against certain conditions that could be detrimental to compressor life. The switch shuts
the unit down in the event of loss of refrigerant, fan motor failure, evaporator freeze-up and
airflow blockage. The switch automatically resets when the pressure rises to normal operating
pressures. The display will show "LP" if this switch is tripped.
The low-pressure switch will shut the heat pump down when the evaporator starts to freeze.
When the unit starts to freeze the low-pressure switch will be tripped, causing the display to read
"LP" This will prevent the evaporator from becoming damaged or deformed.
If the air outside the heat pump is not warm enough to produce heat, the system will shut down.
The actual point at which your unit will shut down due to low temperature varies depending on
which model you purchased, current weather conditions, and the amount of sunlight reaching the
heat pump. The shutdown can occur anywhere within a wide range of temperatures, usually 45°F-
55°F. This is not a "fixed" range. We stress that climate conditions, sunlight, and various models
respond quite differently to low ambient temperature. A shutdown occurs because low
temperatures will activate the systems low-pressure safeguard switch (digital thermostats will
display a code "LP".) The unit will start up again when the temperature has raised enough to reset
this switch. Note: Low ambient temperature does not necessarily affect the Chiller models
or the cooling cycle of the heat/cool units.
If this post has helped you, please take the time to vote positively for me on this site. If you need additional help, I can be reached @: firstname.lastname@example.org
Oct 23, 2010 | Hayward Heatpro 81k Btu Swimming Pool Heat...
Sep 05, 2010 | AEG S72348KA ST STEEL Refrigerator
Sep 29, 2009 | Heating & Cooling
Mar 10, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
16 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: