Question about Amana Heating & Cooling
Try tapping firmly on the gas valve while it is trying to open. If it ignites, you will definately need a new gas valve in the near future (but this little trick might get you by for a while). If not, try using a meter, to make sure you are getting 24v to the gas valve. If you are getting 24v to the gas valve and it is not opeining, you have a bad gas valve. If you are not getting 24v to the gas valve, you have a different problem like a bad transformer, ignition box, or circuit board.
Posted on Dec 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 12, 2014 | Heating & Cooling
Nov 18, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Oct 10, 2012 | Amana GMVC80905CX Gas Furnace
Nov 28, 2011 | Heating & Cooling
Jun 12, 2011 | Amana Ovens
Feb 02, 2010 | Coleman Propane Forced Air Heater...
Dec 29, 2009 | Heating & Cooling
Aug 26, 2009 | Ovens
Dec 24, 2008 | Amana AGDS902SS Gas Kitchen Range
Dec 02, 2008 | Amana Heating & Cooling
360 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: