Question about Amana Air Conditioners
Try tapping firmly on the gas valve while it is trying to open. If it ignites, you will definately need a new gas valve in the near future (but this little trick might get you by for a while). If not, try using a meter, to make sure you are getting 24v to the gas valve. If you are getting 24v to the gas valve and it is not opeining, you have a bad gas valve. If you are not getting 24v to the gas valve, you have a different problem like a bad transformer, ignition box, or circuit board.
Posted on Dec 16, 2008
Tips for a great answer:
Mar 09, 2014 | Air Conditioners
Nov 28, 2011 | Air Conditioners
Jan 25, 2011 | Air Conditioners
Dec 28, 2010 | Goodman Air Conditioners
Mar 27, 2009 | Ruud Central System Air Conditioner
Jan 13, 2009 | Air Conditioners
Dec 02, 2008 | Amana Air Conditioners
Nov 12, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 10, 2016 | Amana Air Conditioners
359 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: